Midwest hot tub disconnect box ground bar?
Asked Nov 4, 2009, 12:16 AM
I've recently taken on the adventure of setting up the basic wiring of a Midwest hot tub breaker box "service disconnect" with 50 AM GFCI breaker installed. The disconnect box I purchased has an aluminum bar (ground I assume) inside the box that can be connected (?) to one of the three terminals (obviously not the hot so that knocks it down to two). My logic tells me this aluminum bar should be connected to the ground bar along with all other green wires... anyone seen one of these before?