Connections for Midwest Electric 60A GFCI Spa Disconnect Panel
Asked Feb 15, 2011, 09:34 AM
I'm installing a spa with a Midwest Electric 60A GFCI spa disconnect panel (#UG412RMW260P)between the spa and the house main service panel, but I'm confused which lugs in the disconnect box to connect the "hot" wires (Red & Black) to from my house service panel? This panel has two sets of lugs below the GFCI breaker and I'm not sure if one set is for "black" and the other for "red" connections, or if one lug set is for one set of black and red connections and the other for a second set of black and red connections. Is anyone familiar with this panel's configuration and can lend some advice? Picture of the panel is attached.