My 12s16 102 zone valve is not closing with thermostat setting change. How can I get a manual or t-shooting tips?
Add your answer here.
Check out some similar questions!
White rodgers thermostat black and white wires [ 1 Answers ]
We have a very old white roger thermostat for our gas furnace and are replacing it with a honeywell rth2310. Our current thermostat only has two wire one balck and the other white. Where do I make the connections.
I have a weil-mclain boiler. The zone valve opens but no heat in zone. What do I do? [ 1 Answers ]
Have replaced the zone valve actuator, but it doesn't seem to be fixing the problem. What else can I do?
White Rodgers gas valve 36e troubleshooting [ 3 Answers ]
I have a Lennox G23 furnace with a White-Rodgers 36E24-204 NG valve that continually is tripping the limit switch, due to a condition where the pilot is putting out way too much flame. I can see areas on the plate where the limit / rollout switch sits, and the flame has deposited large amounts of...
White-rodgers thermostat [ 1 Answers ]
My white-rodgers thermostat read "81" and will not work, batteries have been changed, what is wrong with it?
Replacing White Rogers Zone Valve Power Head [ 1 Answers ]
I recently replaced the power head on a WR zone valve. The valve is working properly but since the change the heat, although hot, lacks any force coming from the base boards. I lost a small amount of water from the boiler when I replaced the valve and am wondering if I lost too much. If so how...
View more questions Search