Oil fired hot air furnace. When unit is off for an extended time it will have delayed ignition on start up. Pump has been replaced because it failed a vacuum test. New nozzle and electrodes, new filter. If thermostat is set at normal (68*) it cycles fine. Problem is only when thermostat is turned way down and the unit totally cools.?