Goodman 95% 2 stage furnace. LED code says pressure switch is stuck open.
1) Changed switch.
2) Jumped Limit switch.
3) Changed PCB.
Same error code. 3 blinks "code says pressure switch is stuck open"
Can You Guide me further
Add your answer here.
Check out some similar questions!
Goodman furnace troubleshooting [ 7 Answers ]
I put a new board in a GMP070 and the inducing fan motor kicks as normal, then the HSI starts to light but the whole board goes dead within 3 seconds.
Troubleshooting goodman furnace [ 1 Answers ]
The flame sensor keep burning out and only run for a couple of minute . Maybe the condensation trap is fully of dirt
Goodman furnace troubleshooting/pgj036100-1 [ 1 Answers ]
It is a goodman gas pack unit Model PGJ036100-1 the burner will come on and burn for about 5 minutes then shutoff the high limit switch is not tripped. The burner will re-light and burn for 5 minutes again and keeps doing this over and over.
Goodman furnace troubleshooting [ 2 Answers ]
I went away for a couple of days and returned to a cold house. I have a Goodman Model HCC075ND4R that has Electronic Ignition with Relay + VR80204 - S8600H Control. I can not get it to fully ignite. It tries to ignite over and over again. I see a single blue flame for a short time, but not main...
Troubleshooting Goodman ac unit [ 1 Answers ]
We have a MF house with an older (1999) Goodman ac unit. My partner is pretty handy but neither of us knows anything about this kind of stuff. For a few days the unit was running but not cooling very efficiently, so we thought it might be a filter or something, and went poking around. He found 2...
View more questions Search