Gas furnace, 80% effiency. Not sure of the name brand. When furnace is running for a little while, the burners will kick off while the blower motor keeps running. After a short time the burners kick back on. This cycle repeats itself until the temperature at the t-stat is reached. Is it possible for fan limit switch to be bad?