# Blower motor won't turn off

I have a Carrier central air and furnace model 28GS 036 000. This problem began with turning the furnace on for the first time this season.

With the thermostat off and the fan set to auto. The blower motor keeps running. Adjusting the temperature on the thermostat and selecting cool or heat does result in the AC and furnace turning on, respectively, so at least that much of the thermostat is working. Disconnecting the limit control (brown and red wires) does not turn the blower off. I can turn the blower off by turning off the "blower door switch" (name given the switch on the wiring diagram) at the furnace, but turning off this switch prevents the burners from igniting. Everything worked fine in summer (AC and blower), so obviously something is broken.

Last edited by spider; Oct 26, 2005 at 05:08 PM.
Search this Question
 fredg Posts: 4,930, Reputation: 674 Ultra Member #2 Oct 27, 2005, 05:34 AM
Blower motor keeps running
Hi,
I would call a heating/air conditioning repair person. It could be a solenoid switch on the motor, gone bad, and not allowing the switch to shut off automatically.
My own heat pump (both ac and heat) would not go through its defrost cycle, at the start of last winter. My heat pump repair person found a bad solenoid switch, replaced it, and now the defrost cycle works fine.
 labman Posts: 10,580, Reputation: 551 Uber Member #3 Oct 27, 2005, 06:11 AM
It is likely a simple matter of the relay that controls the fan is stuck. That used to be a fairly simple matter to fix, but on the newer furnaces the relay is on a control board and much more difficult diagnose and replace. The whole board can easily be replaced if you very carefully note where all the wires go. Unfortunately, they cost an arm and a leg. If that is where the relay is, replacing the board will fix the problem even if it is something other than the relay. Calling a professional could add $100 in labor to what may take a half hour. A dealer for your furnace should have the board. If not, running the furnace as it is, shouldn't hurt anything while waiting for one ordered on line. Shuting off the blower door switch kills all the power to the furnace protecting you while servicing the filters. Makes diagnosing problems harder too.  spider Posts: 5, Reputation: 2 New Member #4 Dec 15, 2005, 06:40 PM Thanks Labman Thanks labman. Finally got around to fixing it. Installed a new board bought from the internet.$100 cheaper for the part then from the local dealers. Took two hours. Took my time, because I've destroyed too many things rushing. Works beautifully.

 Question Tools Search this Question Search this Question: Advanced Search

## Check out some similar questions!

Carrier furnace blower motor won't turn off [ 5 Answers ]

I have a Carrier central air and furnace(furnace model 58GS050-3), it was built around November, 1985. It has carrier air conditioner indoor cooling coils box model 28AC030-911 laid on top of the furnace. Everything was working until one week ago. Now with the thermostat off and the fan set to...

Furnace Blower Fan Won't Turn Off [ 3 Answers ]

Last night I installed a brand new programmable Honeywell to replace my the ancient mercury Honeywell that was on the wall. I have a 20+ year old forced air gas with central air. The side effect has been that the furnace blower will not shut off. Whether the system is in "heat" or "cool" or...

Blower for furnace won't turn on [ 2 Answers ]

I have just re-lit my pilot light for the winter. The furnace is turning on with the thermostat set, but the blower isn't. If I put the blower to manual it turns on, but not in the auto setting. What do I need to do?

A/C Loud Buzzing - Blower Motor won't turn on [ 2 Answers ]

My air handler is making a loud buzzing noise when it attempts to engage. The blower motor will not turn on, although the motor and attached "squirrel cage" appears to turn okay, so I'm guessing the bearings are okay. Is this a capacitor problem, or am I likely to need a new compressor? The unit...

Furnace blower won't turn on [ 8 Answers ]

I have a Bryant 395C furnace. The blower won't come on even when thermostat fan switch is set to "on." I've verified that I'm getting 24V AC between terminals marked G and C on the furnace. Blower has 3 wires going into circuit board on furnace. These are colored red, black, and white; red is...