Hi all. I currently have a 30Amp breaker on 10 gauge wire for the air handler and heat strip. This was a new install and the local inspector seems to think that 30amps is not enough. I took a picture of the specs and uploaded below. What breaker/wire is needed to be in compliance? Any help is greatly appreciated.
Note: Heater Kit is HKR-05