Why Would My Common Wire be Carrying 120Volts When Hooked Directly To Ground Bus In box? Only Two Rooms In The House Affected.
Add your answer here.
Check out some similar questions!
20 Volts Neutral to Ground & 100 volts Neutral to Hot [ 1 Answers ]
My outlets that have been working fine in my new house for 12 years suddenly went dead. I checked the breaker and it was not tripped. I measured the voltage and found 100 VAC from neutral to hot. I then measured Neutral to ground and found 20 VAC and 120 VAC from Hot to ground. Some how I am...
Black to white wire problem only getting about 60 volts not 120. Red to white is 120. [ 2 Answers ]
I am having a wire problem with my hot tub. Had hot tub tech come and he said the problem is in the wiring from the house to the sub panel. He said that the Red to White is reading 120, but the Black to White is only 60. Together the Red to Black is only 180 and we need 240. What could be the...
Can I get 120 volts from a 208v 4-wire service? [ 1 Answers ]
Changing out 208v high bays to 120v LED high bays. I want to know if I can just jump off one leg of the 208v for my 120v fixture.
Stratmando, thanks I don't have 120 volts between Hot and Neutral. I have 120 volts [ 2 Answers ]
Stratmando, thanks I don't have 120 volts between Hot and Neutral. I have 120 volts between hot and ground Also have 120 volts between Neutral and ground How far in the wiring do these types of problems reach into the wall?
120 volts between utility supplied neutral and ground? [ 1 Answers ]
I'm troubling shooting the lighting and the entrance to our community and have run into a problem. I thought I was just going to replace some bulbs, maybe a ballast, but things have gotten worst quickly. Turns out that with the main circuit off I still have 120 between the neutral and ground. I...
View more questions Search