devarajan7 Posts: 1, Reputation: 1 New Member #1 Jan 28, 2009, 04:09 AM
How to calculate the short circuit current flow in a three phase circuit
How to calculate the short circuit current flow in a three phase circuit?
 sathe1963 Posts: 97, Reputation: 4 Junior Member #2 Apr 19, 2009, 08:21 AM
To calculate short circuit current flow in a 3 ph. Circuit, we should know % impedance of source like transformer or generator. Fault mva = base mva / % impedance. On obtaining fault mva, we could find out a.
 I Newton Posts: 110, Reputation: 8 Junior Member #3 Jan 4, 2010, 02:37 AM

In short:

If the impedance of the transformer is 5%
If the full load current of the transformer is 1000A
The short circuit current is 20 times the full load current

i.e. short circuit current = 20,000A
 anasmemon Posts: 3, Reputation: 1 New Member #4 Mar 10, 2011, 01:52 AM

STC is maximum fault current that a system is designed to withstand.For obtaining STC it will be as following example.

Conider a 10 MVA transformer with 6.5% Impedance. System voltage is 13.8/4.16KV. Now Fault MVA = base MVA/PU Impedance

So Fault MVA=10/0.065=153MVA

Now Fault Current = 153*1000/(1.73*4.16)=21259A = 21KA

I hope this can help

 Question Tools Search this Question Search this Question: Advanced Search

## Check out some similar questions!

Current transformer - short time withstand current [ 4 Answers ]

Hi, For ring-type (window-type) CT, do we need to size the CT short time withstand current at the same or above the system short time withstand current (short circuit level)? Any reference/technical explanation? Thanks!

HT Current line tripper when 2 phase [ 2 Answers ]

Dear mr, Please need a information about any instruments for cut off the current line from main HT lines when there is a 2 phase instead of 3 phase because our all the instruments are 3 phase and when there is 2 phase the contacter for the instruments will burn out. Thanking you,...

Short circuit lighting [ 2 Answers ]

Is there a way that you can (safely) make a flourecent light short out like they do in scary movies and old buildings. We are putting together a haunted house and would like to use this effect.

Short circuit current fault [ 1 Answers ]

I have quite a simple system. Contains one substation, feeder pillar and 3 houses. I have calculated the short circuit current that the transfromer in the substation can deliver but is there any one that can help me with finding the equations to calculate the short circuit current level supplied by...

Hi, I'm Peping: I have 90 pieces of single phase loads with current of 2 Amperes. This will be loaded to a 3 phase transformer, Wye connected having a line to line voltage of 220 Volts. What will be the size of the transformer required for the mentioned loads? Many thanks, Peping