Add your answer here.
Check out some similar questions!
What happen if you connect some grounds and neutral to the neutral bus bar and the do [ 1 Answers ]
The same conect some grounds and neutrals to the ground bus bar just using whichever bus bar is closest to the breaker so the wires don't have to travel all around the breaker box is that OK and safe to connect wires like that thank you
220 Volt GFCI Operation without Neutral [ 5 Answers ]
I am installing a 220-volt circuit consisting of two (2) #6 conductors and a #10 ground via rigid conduit to a 50-amp Hot Tub. I have also run a bonding wire to the load center which is within 5-feet of the hot tub. Inside the load center the neutral and ground have been bonded. I didn't run a...
Open neutral on gfci and 1 other outlet [ 2 Answers ]
I have a GFCI outlet that wires to another outlet and both outlets have stopped working and I'm getting an open neutral indication at both oulets. The outlets are on the same circuit as a double wall switch one of which is a 2 way(turn off or on from different locations). The switches work fine...
30amp GFCI to 50amp GFCI [ 1 Answers ]
I have a square D panel box with 200 amp service coming into the house. I have a square D 30 amp double pole gfci breaker that was put in last year for a hot tub. I am now getting a new hot tub, and it requires a 50amp gfci breaker. The 30amp currently in place says type/tipo HOM. It is...
When adding a GFCI disconnect for hottub, should I replace GFCI in service panel? [ 4 Answers ]
I have a hottub now but without a disconnect. Its simply a 6/3-50 amp wire that runs from the hottub to a 50amp GFCI inside the house main service panel. I want to install a disconnect 5-10 feet from the hottub. I bought a disconnect box that already has a GFCI inside of it. Should I have bought...
View more Pools - Spas & Saunas questions Search