Points on pressure switch stay in the closed position and won't kick out when pump stops, therefore the pump won't restart. Have any ideas?
Add your answer here.
Check out some similar questions!
York residential furnace pressure switch problem code stuck switch [ 1 Answers ]
I have a york furnace P2MD12H06401A after 1 hour it shuts down and gives a 2 flash error for a stuck pressure switch. The switch is new can it be wired wrong? The old one had 2 white wires piggy back and 1 blue wire. The new switch has 3 separate terminals
Points keep burning out on pressure switch [ 2 Answers ]
Points on pressure switch keeps burning out on one side of the switch. Is the switched wired wrong or do I have a more serious problem
Toggle Switch Rated for Tools. Six Connection Points. How Come? [ 5 Answers ]
Hi, All! I just bought a new, generic switch for a bench mounted power tool that I have. It's a toggle switch. I needed something that had a ground connector. I figured out how to connect things up and everything is working fine! However, this switch has six connection points on it. I'm...
Deep well, pressure tank/switch not building pressure [ 13 Answers ]
The only way I have water pressure is to leave the power on! I have replaced the 5 gallon pressure tank (28psi when void of water)/fittings/pressure gauge and tried 3 new 30/50 pressure switches and the problem remains the same. With the power off, the pressure drops to 0 (not 30). When I...
Square D pressure switch wiring melting points. [ 7 Answers ]
Hi everyone, I am having problems with my well this week and right now have no water at all. I saw earlier in the week that the old pressure switch contacts were in very bad shape so I cleaned them but a day later it quit working. I bought a new switch this morning and put it in after about 10...
View more questions Search