I have a 200 amp GE panel. On both sides, alternating breakers are inoperable. Does this mean that 1/2 of my 200 amp main breaker is blown? Thanks
Add your answer here.
Check out some similar questions!
Running two 100 amp main panels from a 200 amp service [ 27 Answers ]
Greetings! I live in a rural country area. The electric company will be installing a pole, meter, and 200amp service with disconnect at pole. (It will require 50 foot run of service cable from pole to main load center in mobile). Currently the double wide has a General Electric 100amp Main...
2 main panels from 1 200 amp service [ 3 Answers ]
Can I have the main 200 amp service and off the lugs on top run wire to another main panel instead of sub panel?
Running two 100 amp main panels from a 200 amp service single lug meter [ 1 Answers ]
I have a 200 amp meter with single load side lugs. Presently my house is tied to these lugs. I'm building a remote garage which will require a 100amp feed. Tieing the house to the garage is not doable due to the location of the driveway. I would like to have the existing 200 amp meter feed...
400 amp service, 2 200 amp panels, 320 amp meter socket [ 10 Answers ]
Hi, this is my first post here, but I have been reading a lot and have already learned a bunch. I want to thank TK already and hope you reply to this. I am in the process of designing my electrical system for my new home. I have some electrical experience, but am by no means a pro. I am...
400 amp service with 2-200 amp panels & 320 amp socket [ 6 Answers ]
Hi TK. I am running 400 amp service into my new contruction home. The electric compnay is running a single 400 amp line to the meter. I have to split it to the two panels at that point. You had told me once before that I need a 320 amp meter socket and then run 2-200 amp lines to the separate...
View more questions Search