Add your answer here.
Check out some similar questions!
GFCI will not reset-red buttons keeps popping [ 3 Answers ]
My one GFCI outlet pops its red button occasionally. :( Now it is has popped with nothing plugged into any of the outlets that I can determine are connected with it and it will not stay in - keeps popping out. What does this indicate, is it a fire hazard in any way, and what can I try? Meanwhile...
30amp GFCI to 50amp GFCI [ 1 Answers ]
I have a square D panel box with 200 amp service coming into the house. I have a square D 30 amp double pole gfci breaker that was put in last year for a hot tub. I am now getting a new hot tub, and it requires a 50amp gfci breaker. The 30amp currently in place says type/tipo HOM. It is...
When adding a GFCI disconnect for hottub, should I replace GFCI in service panel? [ 4 Answers ]
I have a hottub now but without a disconnect. Its simply a 6/3-50 amp wire that runs from the hottub to a 50amp GFCI inside the house main service panel. I want to install a disconnect 5-10 feet from the hottub. I bought a disconnect box that already has a GFCI inside of it. Should I have bought...
Hot Tub gfci [ 1 Answers ]
The hot tub that I'm installing requires a 240V supply but there are only three connections. The two hot leads and a ground connection, shouldn't there be a lug for the neutral wire also? The gfci breaker has a three wire with a ground (4 wires) on the line side with the white neutral on the line...
Reset button keeps needing to be reset [ 2 Answers ]
The reset button on our oil furnace needs to be reset every 10 to 14 days. What can be the problem? We are leaving for the holidays and I'm concerned that we could come home to frozen pipes.
View more Electrical & Lighting questions Search