2 ton for 600 sq ft huh. I hope you live in the deep south with poor insulation.
Yes that motor is over rated (to big). It will be loud, use more energy, and flood the condenser. Which will require more refrigerant to keep the head pressure up and thusly the suction pressure, even with a TXV type metering device.