View Single Post
Posts: 10,418, Reputation: 2515
Mar 13, 2012, 07:41 AM
You are allowed a maximum 360 degrees of bends in the conduit(4 90's), if you need more bends between runs, you will need a box or LB. Wires can be looped with no break in the wire, I see you were talking about a Disconnect.
We'd like to understand what you find wrong with
What's inaccurate about this answer? Say it in 25 words or less here and/or reply in the thread with more detail. Please focus on the content not the person!
Link to a credible and well-known source. You can provide a URL or simply describe the source.
View Public Profile
Send a private message to Stratmando
Find all posts by Stratmando